Maintenance free and accurate dosing pump
ProMinent Electronic Dosing Pumps type Concept CC3 and B are driven by a solenoid and controlled electronically. The only moving part in the pump is the solenoid armature which has a maximum movement of 1.25 mm only and this makes the pumps virtually wear and tear free. These pumps consume minimum power and the out put from the pumps can be controlled by adjusting the frequency as well as the stroke length. The output can also be controlled automatically through pulse signals or 4-20 mA signal. The Concept CC3 pumps are available upto a capacity of 24 l/hr while the B pumps are available upto a capacity of 60 l/hr. The liquid ends are available in PVC, Polypropylene, Teflon and Stainless Steel.
ProMinent Electronic dosing pumps are maintenance free, accurate and consume minimum amount of power.
Field of application
The following list of applications are general examples of generally suitable applications for this product. Please contact your local sales representative to talk about the applicable use of this product in your specific case / environment.
Field of application
- wastewater treatment
- process water
- acid dosing
- chlorine dosing
- SMBS dosing
|Pump type||Delivery rate at max. back pressure||Delivery rate at medium back pressure||Stroke rate||Suction lift||Connection size|
oØ x i Ø
|Motor rating||Shipping weight|
|B 20.001||20||1.44||10||1.87||6600||6||8 x 5||190||7.5|
|B 20.005||20||4.22||10||5.3||6600||6||8 x 5||190||7.5|
|B 10.006||10||5.76||6||6.4||6600||6||8 x 5||190||7.5|
|B 13.010||13||9.9||6||14.5||6600||6||8 x 5||190||7.5|
|B 06.014||6||14.5||3||17.0||6600||6||8 x 5||190||8.0|
|B 08.013||8||12.95||4||18.0||6600||5||12 x 9||190||8.0|
|B 04.018||4||18.0||2||20.0||6600||5||12 x 9||190||8.0|
|B 04.023||3.5||24.0||2||40.0||6600||2||12 x 9||190||8.5|
|B 02.040||2.0||40.0||1||42.0||6600||2||12 x 9||190||8.5|
|B 02.055||1.5||54.6||1||60.0||6600||1||DN 15||190||12.5|
Downloads for ProMinent Electronic dosing pump type 'B'
The server is temporarily unable to service your request due to maintenance downtime or capacity problems. Please try again later.